TQS3 E - Bareboard RS485 thermometer
Bare board of the TQS3 Thermometer. It measures temperatures in the range from -55 ° C to +125 ° C and the measured value is sent in degrees Celsius. The thermometer has very low consumption and communicates via Spinel or MODBUS protocols. The TQS3 intelligent temperature sensor can be connected to other modules by a single bus, which can be up to 1200 m long.
New feature: The users can now switch between the Spinel and Modbus RTU communication protocols using ModbusConfigurator software.
The thermometer communicates via RS485 using the Spinel or MODBUS RTU protocol. In the case of Spinel protocol, the thermometer can be connected to a joint communication link with other devices of our company – most of our devices communicate via the Spinel protocol. TQS3 can communicate via the binary as well as ASCII format of the Spinel protocol. ASCII format is very simple – the instructions can be sent and the measured values read to/by some of the many terminals for serial communication. For machine processing, it is preferable to use the binary format of the protocol. For both versions, the documentation provides specific examples.In the case of communication by the MODBUS RTU protocol, the thermometer can be easily integrated into the systems that communicate via this industrial protocol.
- Thermometer measuring temperatures from -55 to +125 °C.
- 0,1 °C resolution
- Accuracy ±0,5 °C from -10 to +85 °C, otherwise ±2 °C
- Communication line RS485 - up to 32 devices can be connected on a single bus (even more when a repeater is used)
- Bareboard to be embeddded to your device
- Spinel or MODBUS RTU communication protocol (to be selected by the user; the factory default setting is the Spinel protocol)
- Low power requirements (typically 2 mA)
- Wago terminal connection
Example of TQS3 connected to a PC through USB or COM port.
Example of TQS3 connected to a computer network (Ethernet, Internet).
Power: To power all converters and thermometers 12V DC PSU is enough for most cases.
Connection wires: To connect thermometers, power supply and converter, TP cable (Cat5e) is recommended. Use one pair for RS485, and other wires for power supply.
Software: To watch and log the temperatures from TQS3 sensors, Wix software can be used (freeware). Other option is user made software. The protocol is well documented and very simple.
Complete datasheet (manual). Including Spinel and Modbus RTU protocol documentation.
File size: 1012 kB
Wix - Free version of measurement software, version 220.127.116.11
Software for measurement, storing values, controlling and viewing measured-out values from Papouch s.r.o. devices (or others if integrated with for example MODBUS).
(Restrictions in the free version can be removed by purchasing a license.)
Go to Wix main page...
File size: 2.4 MB
Simple utility to set-up address and communication speed of your devices with Spinel protocol.
File size: 339 kB
Searching utility. This will search your RS485 line and find all devices with Spinel protocol you have connected. It can also switch TQS3 to TQS1 mode and vice versa.
File size: 506 kB
Software designed for switching communication protocols in our devices, primarily between Spinel and Modbus RTU.
File size: 452 kB
Do you have any question or a suggestion? We would like to hear it!
If you have any question, suggestion or just a note, we are pleased to hear all about it! Just write it in the following form and send it, simple as that. You can also contact us or our distributor by phone or e-mail, all can be found in contacts.